News: USA - remanufacturing can provide the fastest reliable option
When a 46-year-old GE transformer at Duke Energy's W.C. Beckjord Generating Station Unit 5 failed, Duke corporate engineer John Flick pressed into service a 40-year-old spare transformer of questionable reliability, and sought options.
Friday, 5th June 2009
A new transformer was not an option, as Flick needed a fast solution. ABB's TRES (Transformer Remanufacturing and Engineering Services) organization, however, delivered just the option he needed. ABB TRES offered to redesign and upgrade the failed transformer by replacing the necessary components to make it new and reliable again - in only 15 weeks. Beckjord is a 1,124-megawatt coal-fired power plant near Cincinnati. The plant is located in the ReliabilityFirst region. The mission of the ReliabilityFirst organization is to preserve and enhance electric service reliability and security for interconnected electric systems within its geographic area, which spans 13 states and the District of Columbia, encompassing mainly the Mid-Atlantic and central areas of the United States, representing nearly 40 percent of the eastern interconnected electric network. Since ABB owns the original drawings and manufacturing information for more than 70 percent of the transformers operating in North America, the ABB TRES team quickly retrieved the Beckjord Unit 5 transformer's original drawings and manufacturing details from the archives. With this information, transformer service experts explained to Flick exactly how the transformer could be remanufactured to fully take advantage of ABB's TrafoStar technology. As soon as ABB TRES received Duke's purchase order, the redesign began. Using the transformer's original drawings, the ABB TRES team had performed the redesign, ordered materials and started production of new components by the time the transformer reached the ABB TRES factory in St. Louis, Mo. The original five-legged electrical steel core was also cleaned and qualified for reuse. Current transformers were rewired and qualified for reuse. In addition, two conservator tanks were refurbished and new air cells were installed. All other components were replaced. The ABB staff specified the windings, pressure plate assemblies, core insulation, bushings, de-energized load tap changer, cooling system, controls, buss bars, piping, gauges, oil pumps, valves, gaskets, junction boxes, conduit and wiring. When assembly was complete, ABB TRES tested the transformer on its test floor in St. Louis to ensure that no defects were present and the up-rated transformer would perform as designed. All performance expectations for the new transformer were met or exceeded during the testing process. Since all organic materials susceptible to aging were replaced with brand-new materials, the remanufactured transformer would be expected to have a life expectancy equal to, or greater than, a new transformer. The remanufactured transformer came with a warranty that lasts 36 months from the time the transformer was assembled on site.
The European Remanufacturing Council (CER) is open for business
The European Commission has asked for a coordinated voice from EU-28 remanufacturing businesses. The Conseil Européen de Remanufacture will represent small and large businesses from all remanufactured product sectors. Register your interest now!